Published on March 1, 2014
1 Refrigeration & Air Conditioning M S Steve Assistant professor Dept of Mechanical Engineering Amal Jyothi College of Engineering
2 Refrigeration System The mechanism used for lowering or producing low temp. in a body or a space, whose temp. is already below the temp. of its surrounding, is called the refrigeration system. Here the heat is being generally pumped from low level to the higher one & is rejected at high temp. email@example.com
3 Refrigeration The term refrigeration may be defined as the process of removing heat from a substance under controlled conditions. It also includes the process of reducing heat & maintaining the temp. of a body below the general temp. of its surroundings. In other words the refrigeration means a continued extraction of heat from a body whose temp is already below the temp. of its surroundings. firstname.lastname@example.org
Major applications • Food processing ,preservation & distribution. • Chemical & process industries. • Special applications such as cold treatment of metals , medical , construction etc. • Comfort air conditioning email@example.com
5 • Refrigerating system • Refrigerated system • Refrigerant – working fluid The equipment used to maintain a lower temperature inside the system than its surroundings is known as refrigerating system & the working fluid used inside the system is known as refrigerant. • TYPES OF REFRIGERATORS ▫ Air refrigerator ▫ Vapour refrigerator firstname.lastname@example.org
6 Unit of refrigerating capacity • The rate of heat absorbed from a body to be cooled is called refrigerating effect. • Refrigerating effect: It is the amount of heat energy removed per unit time from the space to be cooled by the refrigeration process. It is expressed in kw or kJ/s. It is also called capacity of a refrigerator • The main unit of refrigeration is tones of refrigeration (TR). • It is the rate at which the heat is removed from one U.S tone of water at 0 d.c to ice at 0 d.c in 24 hrs. email@example.com
7 • The rate of heat absorbed by the system from the body to be cooled, equivalent to the latent heat of fusion on 1ton of ice from and at 0 d.c in 24 hours is called one ton refrigeration. • One ton of refrigeration is the rate of heat absorbed by the system from the body to be cooled ,equivalent to the latent heat of fusion of one ton of ice, from and at zero degree Celsius in 24 hours. • In general 1 ton refrigeration is equivalent to 3.5167 kJ of heat removal per second. firstname.lastname@example.org
8 Coefficient of Performance (COP) COP= desired refrigerating effect ________________________________ work spent in producing the refrigerating effect COP of a refrigerator will be greater than unity email@example.com
• Coefficient of performance (COP) It is the measure of the effectiveness of the refrigeration system. It is the ratio of refrigerating effect (Q) to the input work required to produce the effect(w) . COP =refrigerating effect/work input = Q/W • Relative COP: It is the ratio of actual COP to the theoretical COP. firstname.lastname@example.org
COP & EFFICIENCY • COP indicates the effectiveness of a refrigerator or heat pump. • For refrigerator the desired result is extraction of heat from space. • Generally the value of COP of refrigerator is more than unity but the value of efficiency is less than unity. • It is for this reason the term COP is used for rating the refrigerator. email@example.com
11 Thermodynamics of a Refrigerator T< T 1 2 Source T2 Q2 COP (coefficient of Performance)= Q1/ W Refrigerator Work W Q1 Sink T1 • For refrigerator maximum Q1 should be taken out with minimum expense of W ,so performance of refrigerator is evaluated by COP (coefficient of Performance)= Q1/ W. firstname.lastname@example.org
Methods of producing refrigeration 1.Sensible cooling by cold medium. eg :cooling of fish with ice, cooling with cold air /cold water or brine. 2.Endothermic mixing of substances- refrigeration effect obtained is small. 3.Phase changing process such as sublimation ,melting & evaporation - eg: melting of ice produces a refrigeration effect in the surroundings. 4.Expansion of liquids- it is a popular method of cooling. (isentropic & isenthalpic process) email@example.com
Methods of producing refrigeration 5.Expansion of gases.(isentropic & isenthalpic process) 6.Magnetic refrigeration-adiabatic demagnetisation 7.Thermoelectric refrigeration- it is based on the reverse Seebeck effect firstname.lastname@example.org
Air refrigeration system • The air is taken in to the compressor from the atmosphere & is compressed. • The compressed air is cooled to atmospheric temperature in a heat exchanger. • The cooled air is then expanded in an expander. • The low temperature air coming out of the expander enters the evaporator and absorbs heat from the source. email@example.com
Air refrigeration system •. firstname.lastname@example.org
17 Simple Vapour Compression System Evaporator Throttle valve Low pr gauge condenser High pr gauge compressor email@example.com
18 High pressure Low temperature liquid
21 Vapour compression systems firstname.lastname@example.org
22 Parts • • • • Compressor Condenser Expansion valve Evaporator email@example.com
Vapour Compression Refrigeration System
Vapour Compression Refrigeration System • The function of the compressor is to continuously draw the refrigerant vapour from the evaporator and compress it to a high pressure. • Condensor is used to condense the refrigerant from vapour to liquid. • Throttle valve acts as an expansion device. • In evaporator the lower temperature refrigerant absorbs the heat from the space to be cooled and the refrigerant gets evaporated. firstname.lastname@example.org
T-S & P-H Diagram
27 Practical Vapour Compression Cycle. Components of the Practical Cycle
28 A home refrigerator with its door open email@example.com
29 Vapour absorption system firstname.lastname@example.org
Vapour Absorption Refrigeration System • It differs from the vapour compression system only in the method of compressing the refrigerant. • The compressor is replaced by a combination of absorber, generator & a pump. • Ammonia is a very suitable refrigerant for this system email@example.com
Vapour Absorption Refrigeration System firstname.lastname@example.org
33 Vapour Absorption System • No moving parts • Low grade thermal energy like solar energy can be the input energy. • Load variation does not affect system performance. • Environmental friendly. email@example.com
34 Refrigerants • Defined: Any substance capable of absorbing heat from another required substance can be used as refrigerant i.e. ice ,water, brine, air etc. Primary Ref Refrigerants: Secondary Ref firstname.lastname@example.org
They take part in refrigerating systems. eg: Freon Ammonia , Carbon dioxide, Sulphur dioxide etc. First they are and then they are circulated . eg: Chilled water, brine solutions etc. email@example.com
36 Properties of Refrigerants • • • • • • • • Low Boiling Point Low Freezing Point. High Latent Heat. Chemically Inert & stable . Non Flammable Non toxic Should not react with lubrication oil of comp. Should not be corrosive firstname.lastname@example.org
Important refrigerants • Refrigerant is the working fluid used in refrigerators . Commonly used refrigerants are: 1.Ammonia : used in ice plants, large cold storages, skating rings etc. 2.Carbon dioxide : used in marine refrigerators, dry ice making etc. 3.Methyl chloride: used in domestic & industrial refrigerators (now obsolate) 4.Fluorocarbons : Freon -11,12,13,22,113,114, etc. These are used in domestic & industrial applications.These chemicals damage the ozone layer and hence they are being replaced. email@example.com
PROPERTIES OF AN IDEAL REFRIGERANT • An ideal refrigerant should satisfy the following thermodynamic , chemical & physical requirements: a. Thermodynamic properties. 1. low boiling point 2. high critical temperature & low critical pressure. 3.Freezing point should be lower than the refrigeration system temperature to avoid blocking of pipes. b. Thermo physical properties. 1. low viscosity. 2. high thermal conductivity. 3.high latent heat of vapourization. 4.low specific volume. 5.low specific heat. firstname.lastname@example.org
PROPERTIES OF AN IDEAL REFRIGERANT c. Chemical requirements. 1. Should be non inflammable. 2. It should not be toxic. 3. Should be non corrosive to metals. 4.Should be capable of mixing well with lubricating oil. 5.Electric resistance should be high. 6.Leakage should be detected easily. 7.Should be odourless. email@example.com
Domestic refrigerator • Vapour compression cycle is normally preferred over absorption system in domestic refrigerator because of its compactness and more efficient use of electrical energy. • Refrigerant used is R-12 or R – 22. firstname.lastname@example.org
Lay out of an Ice plant email@example.com
Ice Plant • Ammonia is used as the refrigerant. • The high temperature, high pressure ammonia vapours are condensed in a condenser . • The condensed liquid ammonia is collected in a receiver and then expanded through the expansion valve . • As the low pressure ammonia passes through the evaporator coils, surrounding the ice cans in the brine tank in which brine solution is filled, it absorbs heat from the solution and gets vapourized . • It is again fed to the compressor to complete the cycle. firstname.lastname@example.org
Refrigeration Engineers: Job Description & Career Info. Refrigerators may seem like a mundane fixture of everyday life, but refrigeration engineering ...
There are some aspects in which vapor absorption refrigeration system is different from that of vapor compression. The main principle is the same for the ...
1. 1Refrigeration & Air ConditioningM S Steve Assistant professor Dept of Mechanical Engineering Amal Jyothi College of Engineering. 2. 2Refrigeration ...
Welcome to refrigeration.engineering - United Kingdom. Refrigeration is our passion. Search our forum to find more information about HVAC science.
BASICS OF MECHANICAL ENGINEERING (ME-101 F) Lectures on REFRIGERATION AND AIR-CONDITIONING Introduction to RAC Rating of refrigeration machines
Refrigeration Engineer, Business Owner, Manager at Alpine Refrigeration & ... Basic Mechanical Engineering - Refrigeration. 4,645 Views. eramanagrawal.
Amazon.com: basic refrigeration. Amazon Try Prime All ... Basic Mechanical Engineering May 5, 2016. by N.R. Banapurmath & V.S. Yalliwal. Kindle Edition. $ ...
The fourth part of Mechanical Engineering Q & A. This fourth part is totally dedicated to viva questions from the chapter Refrigeration & Air-Conditioning.
Refrigeration Basics 2 - Standard. Refrigeration Basics 2 (Version 2) is available at the original economic price. See the online sample sections and try ...