Published on February 26, 2014
BundGuard FLOODLINE IWS Andel-PPL BundGuard Automatic oil and water separating pump system The Andel-PPL BundGuard system was developed in 1992 specifically at the request of the UK electricity industry who faced serious water removal problems at substation sites all over the country. Since then many thousands of BundGuard units have been installed nationwide protecting the environment and the operator of the site. Any tank, drum or plant containing more than 200 litres of oil must be provided with some form of secondary containment or "bund", to retain leaks, spills or worse. By law the bund must be capable of holding at least 110% of the contents of the main oil tank. Larger oil storage tanks and equipment such as electricity transformers may contain several thousand litres of oil and are likely to be open to the elements. The bund will collect rainwater and, before too long, the holding capacity of the bund will be significantly reduced. Obviously as oil floats on water, once the capacity drops below 100% there is a risk of oil escaping over the bund wall in the event of tank failure. Guidance note for the Control of Pollution (Oil Storage) (England) Regulations 2001 Clause 29 “It is recommended that the water be collected in a sump formed in the base of the bund and removed using a manually operated pump or by baling. A fail-safe automatic pumping system can be used, which monitors the oil and water interface, and automatically activates to pump out only water.” http://www.defra.gov.uk The Andel-PPL BundGuard is a cost-effective, self-contained and easy to fit automatic pump and alarm unit which works continuously and automatically 24 hours, 7 days a week, 365 days a year. Using advanced circuitry and micro controller technology, the system discriminates between oil and water; it keeps oil in and expels water from the containment area. The robust, all stainless steel, pump and sensor unit is located in the sump and monitors the different liquid levels. The control unit activates the pump as required to remove only clean water safe to foul sewer or interceptor (depending on site circumstances). Failsafe systems and a range of visual and relay alarm outputs ensure complete safety and allow onward communication to remote monitoring systems. The use of the Andel-PPL BundGuard system removes the need for regular emptying of the bund by waste contractors thus reducing your costs, environmental impact and carbon footprint. Control Panel Power: 110/230 VAC, 440Watts (total inc pump) Construction: Stainless steel, IP66 rated Dimensions: 320h x 260w x 120d Indicators: LEDs; Mains Supply, Pump Active, High Water Alarm, High Oil Alarm, Pump Disable LCD; Pump Operation Counter Outputs: Mains fail, High Water, High Oil, Pump Disable rated at; 10A @ 230VAC (AC1) 0.1A@ 220VDC (DC1) Fixing: Wall/surface mount via external fixing lugs Sensor Unit Power & Voltage: nominal Construction: Stainless steel, immersion proof Dimensions: 570h x 180w x 70d Fixing: Free standing in base of sump Pump Power & Voltage: 230 VAC (110VAC optional) Construction: Stainless steel Dimensions: 250h x 160w Safety: Thermal trip; self reset Flow Rate: 110litres per minute at 2-3metre head Fixing: Part of the sensor unit The Andel-PPL BundGuard comes complete with a fixing kit (glands, jubilee clips, hose clips and fixings), anti-syphon device and 5metres of 18bar flexible hose. The unit is preconfigured in the factory although some on-site adjustment may be carried out if needed. No further calibration is required. Maintenance should be carried out every 6/12months depending on site conditions. Ideally the sump should measure 60cm x 60cm x 60cm, call us for advice if your sump measures differently. The sump size and capacity affects the efficiency of the pumping system. FM 512048 ISO 9001:2008 E&OE 11r03 Tel: +44 (0)191 490 1547 Fax: 1484 845 www.pollutionprevention.co.uk Tel: +44 (0)+44 (0)191 477 5371000 Email: email@example.com Andel Ltd and BSI registered address Website: www.heattracing.co.uk www.thorneanderrick.co.uk Andel Ltd, New Mills, Brougham Road, Huddersfield, West Yorkshire, HD7 6AZ
Presentación que realice en el Evento Nacional de Gobierno Abierto, realizado los ...
In this presentation we will describe our experience developing with a highly dyna...
Presentation to the LITA Forum 7th November 2014 Albuquerque, NM
Un recorrido por los cambios que nos generará el wearabletech en el futuro
Um paralelo entre as novidades & mercado em Wearable Computing e Tecnologias Assis...
Andel PPL BundGuard Automatic Oil & Water ... Automatic Oil & Water Separating Pump System. ... Oil & Water Separating Pump System - Spec Sheet
Andel-PPL BundGuard Automatic oil and water separating pump system The Andel-PPL BundGuard system was ... The use of the Andel-PPL BundGuard system ...
With a total of 13 gallons of drinking water storage and an automatic ... Share Waterlogic Innowave MAX Water Dispenser Spec Sheet.
AUTOMATIC WATER PUMP ... Water Separating Pump System - Spec Sheet 1. BundGuardFLOODLINEIWSAndel-PPL BundGuard Automatic oil and water separating pump ...
Information about Eltherm ELKM-AG-H Heat Trace Cable - Spec Sheet. Technology. Published on October 1, 2014. Author: TerryMcDonald2
TREATMENT SYSTEMS. OIL/WATER SEPARATORS ... Grey Water Recycling Systems ... ELEVATOR OIL INTERCEPTOR & SUMP PUMP INTERCEPTOR.
Marketing Manager at Raging Waves Water ... Automatic Oil & Water Separating Pump System ... views. Andel ppl oil star tank guard spec sheet Views 69 ...
Information about Chromalox SRME Heat Tape - Spec Sheet. Technology. Published on October 3, 2014. Author: TerryMcDonald2